The development of a high speed compressor working with a low pressure refrigerant could herald a low GWP, non flammable future for air conditioning.
US air conditioning manufacturer Carrier has developed a prototype high speed screw compressor and tested it with a new low pressure, non flammable hydrofluoroolefin (HFO) refrigerant as a potential long term solution for air conditioning systems. As the world moves towards refrigerants with low GWPs, the air conditioning industry has been left largely adrift with, seemingly, no long term, non-flammable alternative for R410A in the dominant Direct Expansion (DX) sector.
The refrigerant R32, along with the recently announced R466A, offer a lower GWP option, but their respective GWPs of around 700 make them unsustainable long term. Industry experts have estimated that under the global phase down regimes average GWPs will eventually need to be around 400.
In addition, popular thinking has previously maintained that, apart from CO2, any potential long-term low GWP refrigerant will exhibit some degree of flammability – a characteristic unsuitable under current and proposed standards and building codes for all but the smaller DX air conditioning systems.
While much of the current development work is being kept under wraps, manufacturers and refrigerant developers are known to have been working on the possibility of using low pressure HFO refrigerants with high speed compressors.
HFOs offer very low GWPs and some, such as R1233zd, are non-flammable under normal operating conditions. R1233zd has already been adopted and proven by chiller manufacturers as an alternative to the use of ozone-depleting R123 in low pressure systems.
However, there are significant challenges for those seeking to deploy these refrigerants in air conditioners. Current scroll or rotary technologies may not be suitable to be applied in such low density refrigerant systems, as large increases in volumetric flows will be required in order to match the cooling capacity of R410A.
US manufacturer Carrier has broken cover to reveal details of what it is calling the Mini Screw. This newly-developed prototype screw compressor employs a new rotor design and a high speed permanent magnet motor to obtain a flow volume of 19.8 litres/s. Screw compressors are well-suited for large volumetric flow, but it required a complete redesign to produce a compressor for typical R410A air conditioning applications.
Details of the compressor’s development and testing were presented in a paper by Carrier engineers Masao Akei, Vishnu Sishtla and Scott MacBain, entitled Mini Screw: the development of a high-CFM compact compressor for LGWP A1 low pressure refrigerant, presented at the 10th International Conference on Screw Machines in Germany in September.
The choice of refrigerant for the tests is a surprise. In this particular test, Carrier was working with a Chemours development refrigerant known as DR-12. The Cooling Post believes DR-12 to be the HFO 1336mzz(E). Not much attention has been paid to this refrigerant, so far, but it is said to be be non-flammable and non-toxic. It is currently going through the ASHRAE classification process.
The prototype compressor was designed for a 17.6 kW capacity at 11,000 rpm and 4.4 kW at 2,500 rpm. This was achieved in a body of similar size to current R410A compressors. Tests were performed in accordance with ASHRAE’s compressor testing standard 23.1, and the compressor was said to have been run for more than 800 hours without any issues.
When contacted, Chemours could not confirm or deny our story, nor would it confirm the identity of DR-12. However, speaking generally, Chemours’ Opteon global business director Joe Martinko said: “We are very encouraged by the feedback we have received from the market on DR-12, which has particularly distinctive stability and performance in a wide range of applications, including heat transfer. We look forward to continued product development and testing of this unique offering.”
Carrier’s work is ongoing and you can expect to hear more from other manufacturers combining high speed compressors with low pressure refrigerants in the future.
The research paper: http://iopscience.iop.org/article/10.1088/1757-899X/425/1/012013